Coconut Carbon Cartridge – 0.5 micron
MATRIKX® Pb1® extruded activated Coconut carbon cartridge filters reduce soluble lead using an ion-exchange filter medium with high specificity for soluble lead. Particulate filtration is used to intercept insoluble lead-containing particles. Standard 2.50” O.D. x 10” L filters will reduce lead, meeting the performance requirements of NSF/ANSI Standard 53 protocol for over 2,500 gallons when operating at a flow of 0.75 GPM.
Manufactured with KX®’s proprietary extrusion process, MATRIKX® Pb1® filters offer high levels of chemical reduction in potable drinking water, including chlorine taste and odour. MATRIKX® Pb1® filters meet NSF/ANSI Standard 53, Turbidity and Cyst Reduction, including Cryptosporidium, Giardia, Entamoeba and Toxoplasma.
MATRIKX® Pb1® filters consist of activated Coconut carbon Cartridge particles fused into a uniform block with enhanced adsorptive capacity and efficiency. MATRIKX® Pb1® filters flow in a radial (outside-to-inside) direction, providing increased dirt-holding capacity and low pressure drop. Unlike granular activated carbon (GAC) filters, MATRIKX® Pb1® cartridges will not channel or bypass due to the extreme uniformity of their extruded activated carbon core. Service life of the MATRIKX® Pb1® filter is greatly extended by a pre filtration medium.
- No channeling
- No uidizing
- No bypassing
- Lowest extractables, pure materials of construction
- Maximum service life and resistance to fouling
- Graded density pre ltration design
- Manufactured using FDA-compliant materials
- Color coded molded one-piece gasket and end cap
IMPORTANT NOTICE: Performance claims are based on a complete system, including a filter, housing, and connection to a pressurized water source. This filter must be placed in an appropriate system, and operated according to the system’s specifications in order to deliver the claimed performance. It is essential to follow operational, maintenance, and filter replacement requirements, as directed for each application, for this filter and system to perform correctly. Read the Manufacturer’s Performance Data Sheet accompanying the system and change the filter as suggested. The contaminants or other substances removed or reduced by this water filter are not necessarily in all users’ water.